This unit is installed in a factory in the south of the Netherlands, and has operated reliably for many years.
Due to changes in production and energy requirements the unit has become surplus to the production of the plant.
Scope of supply.
Complete gas turbine package, including:
– Gas turbine skid
– Generator skid
– Acoustic enclosure over gas turbine
– Ventilation air inlet end outlet system
– Combustion air inlet filter Donaldson
– Air inlet ducting
– Gas fuel system
– Lubricating oil
– Air blast oil cooler
– MKII Rustronics controls system
– Bently Nevada vibration monitoring
– GEC Unilec 10 KV 50 Hz generator
– Cooling air inlet and outlet ducting for generator
History of this unit.
The unit has been installed in 1990 and always been maintained by OEM maintenance personal.
The unit has been upgraded to Dry Low Emissions in 2004 by means of a OEM retrofit.
The currently installed gas generator and power turbine has operated only 900 hours since the last full “B” type inspection and is suitable for a further 24.000 running hours before the next ‘C” type inspection is planned.
The currently installed power turbine has operated 36.000 hours and the rotating assembly is suitable for a further 80.000 hours before exchanging.
All maintenance records available.
Expected performance data at ISO conditions and see level.
Asumptions : 100 mm WG inlet loss
175 mm WG exhaust loss
Inlet Temp C -10.0 0.0 10.0 15.0 20.0 30.0
Output Power kW 7250 7157 6698 6472 6227 5761
Heat Input kW 22900 22643 21634 21121 20590 19582
Exhaust Flow kg/s 31.46 30.53 29.50 28.96 28.38 27.20
Exhaust Temp. C 444 461 468 471 475 483